Monthly Archives: October 2018
Posted: October 19, 2018Categories: Installing Filters
How often should filters be backwashed?
As filtration proceeds, the void areas in the medium become filled with particles removed from the water, resulting in pressure drop from the outlet. Flow rates through the filter medium decreases until it becomes insufficient to meet the demand. A partially clogged filter bed also results in deteriorated water quality. At WECO we prefer backwashing done at least every 4-7 days at 10 gpm/sq.ft and the whole house systems are pre-programed for the self-cleaning cycle to occur at 2.00 AM.
One way to make the when-to-backwash decision is to install pressure gauges before and after the filter. Backwashing should be performed when the pressure drop reaches a pre-determined maximum value (typically 15 PSI for whole house systems). Backwash the system on demand by pressing the Regeneration
Posted: October 13, 2018Categories: Importance of Filtering Water
Why do I need a water treatment specialist? Wont some equipment from the store work just fine?
When it comes to water treatment there is no turnkey solution that works for all water sources. The water that is supplied changes throughout the planet while also changing with the seasons. So there may be a setup in New York that works really well on their water source but it might not work well in California. Each water treatment system needs to be adjusted for based on the water that will be processed within the system. So if we want to find the perfect equipment to process our water we need to find a way to figure out what’s in the water. This is where a water sample should be obtained and sent in for analysis.
City Water vs Well Water?
A water analysis is important so a water treatment professional can assist you in what